arXiv:2209.09165v1 [eess.SY] 19 Sep 2022

An ICA-Based HVAC Load Disaggregation Method Using Smart Meter Data

Hyeonjin Kim, Kai Ye, Han Pyo Lee, Rongxing Hu, Ning Lu

North Carolina State University Raleigh, NC 27606, USA {hkim66, kye3, hlee39, hru5, nlu2}@ncsu.edu

Di Wu Pacific Northwest National Laboratory Richland, WA 99352, USA di.wu@pnnl.gov

PJ Rehm ElectriCities of North Carolina Inc.

Raleigh, NC 27604, USA prehm@electricities.org

Abstract—This paper presents an independent component analysis (ICA) based unsupervised-learning method for heat, ventilation, and air-conditioning (HVAC) load disaggregation using low-resolution (e.g., 15 minutes) smart meter data. We first demonstrate that electricity consumption profiles on mildtemperature days can be used to estimate the non-HVAC base load on hot days. A residual load profile can then be calculated by subtracting the mild-day load profile from the hot-day load profile. The residual load profiles are processed using ICA for HVAC load extraction. An optimization-based algorithm is proposed for post-adjustment of the ICA results, considering two bounding factors for enhancing the robustness of the ICA algorithm. First, we use the hourly HVAC energy bounds computed based on the relationship between HVAC load and temperature to remove unrealistic HVAC load spikes. Second, we exploit the dependency between the daily nocturnal and diurnal loads extracted from historical meter data to smooth the base load profile. Pecan Street data with sub-metered HVAC data were used to test and validate the proposed methods.Simulation results demonstrated that the proposed method is computationally efficient and robust across multiple customers.

Index Terms—HVAC system, Independent component analysis, Non-intrusive load monitoring, Smart meter data

I. INTRODUCTION

Load disaggregation is an important technique in distribution system analysis. Its results can be used in many downstream tasks, for example, customer segmentation, resource identification, and rate recommendation. When the sampling rate of available data sets is less than 1-minute, non-intrusive load monitoring (NILM) methods are often used to disaggregate the electricity consumption curves of different appliances. There are three popular data sets used for developing the NILM algorithms: UK-DALE, REDD, and REFIT, the sampling rates of which are 1, 3, and 8 seconds, respectively. However, in practice, inputs to many load disaggregation algorithms are 15-minute smart meter data and hourly weather data. This makes those NILM methods relying on second-level meter data inapplicable.

In recent years, supervised and unsupervised learning methods are increasingly used for solving load disaggregation problems. The main disadvantage of supervised learning-based methods is that labeled data sets are hard to obtain because sub-metered, device-level load profiles are rarely available. Furthermore, generalization of learned knowledge from one distribution system to another is also difficult because of different weather patterns and customer use patterns. Therefore, in this paper, we choose to use the unsupervised learningbased approach.

The majority of unsupervised learning-based approaches are based on the temporal graphical model, especially, hidden Markov model (HMM) [1]–[3]. Appliances are modeled as HMM and the objective is to estimate the most likely states of appliances. However, the main drawback of this method is that problem complexity exponentially increases with the number of appliances. Furthermore, this method is dependent on metering data [4] with a sampling rate faster than typical smart meter data (i.e., 15-minute).

To overcome the aforementioned challenges, we propose an independent component analysis (ICA) based unsupervised load disaggregation method. ICA is a widely used unsupervised method for blind source separation in speech recognition for speaker identification [5]. It solely exploits information on each customer and is independent of data resolution. In [6], ICA was used for heat, ventilation, and air conditioning (HVAC) load disaggregation where smart meter data and wavelet analysis results are used as inputs to represent different frequency components. However, besides HVAC loads, many other appliances also exhibit cyclic characteristics (e.g., refrigerators). This deteriorates the performance of ICA when being used in load disaggregation applications.

Our first contribution is the use of residual load profiles instead of the total load profiles as the inputs to the ICA algorithm. In [7], we show that the mild-day load profile is similar to the base load profile on a hot day. Based on this finding, residual load profiles can be computed by subtracting mild-day load profiles from hot-day load profiles. Because the mild-day load profile includes weather insensitive cyclic loads, the major cyclic component left in the residual load profile is the HVAC load. This significantly improves the ICA disaggregation accuracy.

Our second contribution is the development of an optimization-based, post-adjustment algorithm for postprocessing ICA results to further improve disaggregation accuracy. The algorithm considers two bounding factors for enhancing the robustness of the ICA algorithm. First, we use the hourly HVAC energy bounds computed from the

Fig. 1. Workflow of the HVAC load disaggregation process.

relationship between HVAC load and temperature to remove unrealistic HVAC load spikes. Second, we exploit the dependency between the daily nocturnal and diurnal loads extracted from historical meter data to smooth the base load profile. We used the 1-minute (down-sampled to 15-minute data) Pecan Street dataset [8], where sub-metered HVAC data are available for evaluating the performance of the algorithm.

II. METHODOLOGY

This section presents the overall modeling framework, the computing of the residual load profile, and the ICA and the post-processing algorithms.

A. Load Disaggregation Work Flow

Let P be the daily load profile matrix and p_{i,j} represent the i^{th} (i ∈ N) data sample of the j^{th} (j ∈ M) day, where N and M is the number of data samples in a day and the number of hot days, respectively. Let P^{mild} be the mild-day load profile matrix and p^{mild}_{i,k} represent the i^{th} data sample of the k^{th} (k ∈ K) day, where K is the number of mild days. For 15-minute smart meters data set, N = 96. Thus, p_{1:N,j} is the daily load profile for the j^{th} hot day and p^{mild}_{1:N,k} is the k^{th} mild day.

As shown in Fig. 1, we first remove infrequently used loads (LIUL) (e.g., dryer and electric hot water heater) from each daily profile in P and P^{mild} using the LIUL filtering algorithm introduced in [7]. The load profile matrices with LIUL removed are represented by P̃ and P̃^{mild}, respectively. Next, we calculate the residual load profile matrix, P^{res}, by subtracting P̃mild from P̃ (see Section II-B). Then, Pres is fed to the ICA algorithm (see Section II-C) for extracting the HVAC load profile matrix, P^{HVAC}. Finally, a residual minimization finetuning algorithm (see Section II-D) is used to adjust P^{HVAC} and P^{base} to further improve the disaggregation accuracy.

B. Classification of Hot and Mild Days

We define a mild day as a day with no heating or cooling loads. In addition, we define a hot day as a day with HVAC loads. The method for hot and mild day classification introduced in [7] is based on temperature thresholds. However, some customers will turn on their HVAC even in a mild day, causing some resultant mild days to contain a small amount of HVAC loads. This can significantly reduce the accuracy of HVAC load disaggregation in later steps. Therefore, we improve the method by adding a verification step: power distribution comparison.

As shown in Fig. 2, the distribution of the nocturnal and diurnal base loads in hot days overlap well with the distribution of the loads for mild days. Therefore, by comparing the power distribution of load profiles, we can separate the mild days from the hot days by comparing its power distribution.

(a) (b)

Fig. 2. Comparison of power consumption distributions: base loads in hot days, mild-day loads, and hot-day loads, respectively.

As shown in Fig. 3, the base load profiles, P^{base}_j , in hot days are bounded by the mild day profiles, P^{mild}, so we have

P^{base}_j = P̃^{mild} · β + θ^b (1)

where θ^b is an adjustment vector with N × 1 dimension and β is a multiplier.

Fig. 3. Average load profiles for the actually measured base load (the solid blue line) and the calculated base load using mild-day load profiles (the solid red line). The shaded area shows the ± one standard deviation against the calculated base load load profile.

By subtracting K mild day load profiles from the j^{th} day load profile one by one, we can obtain an ensemble of residual load profiles, represented by P^{res}_j , which is an N × K matrix. Each column of P^{res}_j contains the actual HVAC load profile, p^{HVAC}_j , plus a random power variation, ϵ_j , both of which are N × 1 vector, so we have

P^{res}_j = [ p^{HVAC}_j ϵj ] · A (2)

where A is an 2 × K mixing matrix.

C. Independent Component Analysis

ICA is a widely used unsupervised method for blind source separation in signal processing [9]. ICA has also been used in NILM for retrieving unlabeled sources. To extract P^{ICA}_j from P^{res}_j , we formulated the ICA problem as

P^{ICA}_j = P^{res}_j W (3)

where W is an K × 2 unmixing matrix (the pseudo inverse of A) and P^{ICA}_j is the calculated HVAC load profile for the j^{th} day. Note that the residual load profiles are obtained by subtracting the total load profile of the j^{th} day with K different mild day load profiles, which we proved to bear the similar load shapes as the base load profile of the j^{th} day. Thus, the ICA algorithm only needs to identify a high percentage, cyclic HVAC load profile and a low percentage, highly random end use load consumption from the residual load profiles. This significantly improves the identification accuracy.

Fig. 4. HVAC hourly power consumption with respect to different outdoor temperatures.

D. Fine-tuning of the ICA Results

The estimated HVAC and base load profiles obtained by ICA can be fine-tuned to further improve the load disaggregation accuracy. Note that because we will estimate the HVAC load and the base load for the j^{th} day, the index j is omitted for all variables.

Let p̂^{HVAC} and p̂^{base} be the final estimation of the HVAC load and the base load of hot days, respectively, the objective function of the fine-tuning process can be formulated as

min p,α,β,γ,θ L_{shape} + λ_1 ‖ ‖ ‖θ^h ‖ ‖ ‖^2 + λ2 ‖ ‖ ‖θ^b ‖ ‖ ‖^2 − λ3LPDF (4) subject to:

L_{shape} = ‖ p − p̂^{HVAC} − p̂^{base} ‖_2 2 (5) L_{PDF} = D_{KL}(N (p̂^{base}_{di} , p̂^{base}_{noc})||N (p̃^{mild}_{di} , p̃^{mild}_{noc} )) (6) p̂^{HVAC} = α · p^{ICA} + θ^h (7) p̂^{base} = P̃^{mild} · β + θ^b (8) p̂^{HVAC}

hour = γ1 · T + γ2 · T ⊙ T (9) | | | | 1 4 · 4k∑ i=4k−3 p̂^{HVAC}_i − p̂^{HVAC}_{hour,k} | | | | ≤ ε ∀k ∈ {1, 2, ..., 24} (10) p̂^{base}_{di} = 1 4 · ∑ i∈N_{di} p̂^{base}_i (11)

p̂^{base}_{noc} = 1 4 · ∑ i∈N_{noc} p̂^{base}_i (12)

0 ≤ p̂^{HVAC}_i ≤ p_i ∀i ∈ N (13) 0 ≤ p̂^{base}_i ≤ p_i ∀i ∈ N (14)

where p^{base}_{di} and p^{base}_{noc} represent the nocturnal and diurnal base loads, respectively, p̂^{HVAC}_{hour} is the hourly HVAC load, T is a vector of outdoor temperature, γ_1 and γ_2 are coefficients, θ^h and θ_b are adjustment vectors, and ε is an error margin.

The first loss term calculated by (5) calculates the pointto-point load disaggregation error. The second loss term calculated by (6) represents the similarity between diurnal and nocturnal power consumption distributions of the final base load and the mild-day-computed base load. To compensate non-linearity, the final estimation of the HVAC and the base load, p̂^{HVAC} and p̂^{base}, are scaled by α and β and adjusted by θ_h and θ_b by (7) and (8), respectively. (13) and (14) ensure that, at each timestamp, p̂^{HVAC} and p̂^{base} are both lower than the total load.

As shown in Fig. 4, HVAC load can be assumed to have quadratic relationship with outdoor temperature. To incorporate hourly temperature into the estimation, we first calculate the hourly HVAC load, p̂^{HVAC}_{hour} , by (9). Then, the sum of the estimated HVAC load in each hour is bounded by p̂^{HVAC}_{hour} with a margin of ε in (10).

III. SIMULATION RESULTS

The simulation results and performance evaluation are presented in this section.

A. Simulation Setup and Performance Evaluation Metrics

Pecan Street data sets (including 150 total household loads and the corresponding sub-metered HVAC loads) are used to develop and validate the proposed algorithm. The original data length is 1-year with 1-minute data resolution. We downsample the 1-minute data to 15-minute. The testing data sets are constructed by randomly selected 30 days in summer from 70 customers in Austin, Texas.

To evaluate the fine-tuning algorithm performance, we set up three cases. The first case is without a log-likelihood term, i.e., (6). The second considers the log-likelihood with

Fig. 5. Load disaggregation results for one house in a summer day

the distribution obtained from a single user. The third case considers the log-likelihood obtained from multiple users.

We compare our method with two benchmark methods. The first method (introduced in [8]) is to compute the average of all mild-day load profiles and use it as the base load profile, which can then be subtracted from the total load profile to get the HVAC load profile. The second method is the ICA method without fine-tuning.

The disaggregation accuracy is evaluated using the normalized mean absolute error (nMAE) and the normalized energy error (nEE), computed by

nMAE = 1 M · M∑ j=1 N∑ i=1

| |P_{∗i,j} − P_{i,j} | | Rating

(15)

nEE =

| | | | M∑ j=1 N∑ i=1 p^∗_{i,j} −^M ∑ j=1 N∑ i=1 p_{i,j} | | | | M∑ j=1 N∑ i=1 p_{i,j} (16)

where the variable with ‘∗’ represents the estimated value.

B. Efficacy of Fine-tuning

In this subsection, we compare two cases: with and without fine-tuning. The results are shown in Figs. 5 and 6, from which, the following observations can be made:

• Without fine-tuning, the HVAC (subplot 1) and base load (subplot 2) profiles obtained by the ICA method has large overshoots or undershoots compared with the with fine-tuning case. This is because the ICA results are not bounded.

• As shown in subplot 3, the fine-tuning algorithm uses the temperature-power relationship to derive upper and

Fig. 6. Hourly box plots of load disaggregation errors for summer load profiles (with fine-tuning). The total data length is 30 days.

lower hourly HVAC consumption bounds. This effectively reduces the occurrence of over- and under-shoots, which, consequently, drastically reduces the point-to-point mismatch.

• In Fig. 6, we show the disaggregation error distribution for each hour of the day of a randomly selected load profile, the accuracy of which lies in the middle of all 70 load profiles. The results show that the performance is the best in the early morning and the worst during the lunch and dinner times. This is because there are multiple appliances in use and the cycling of the HVAC unit may be affected by internal heating sources (e.g., heat from cooking) besides the outdoor temperature. The highest error happens at 18:00 with a median nMAE of 0.15. However, most of the demand response programs target at the time period from 15:00 to 17:00, during which, the overall performance of the algorithm is satisfactory.

C. Efficacy of Matching Base Load Distribution

In this subsection, the effect of including constraint (6) in the fine-tuning process (4) is evaluated. As shown in Fig. 7, the ICA identified base load has a larger mismatch than the mild day computed base load (marked as the ”proposed” in Fig. 7) when comparing with the actual distribution. This is further proved by the results shown in Table I. Thus, in the fine-tuning, we can use (6) to correct the ICA calculated base load profile to achieve a more accurate point-to-point match in base load disaggregation.

D. Comparing with the Benchmark Methods

In Table II, the numerical performance of proposed models and benchmark models are compared. It is shown that by adding the fine-tuning as the post-adjustment process, the point-to-point estimation error can be reduced for all three cases compared to benchmark models. However, the accumulated error of the proposed model represented by nEE are about the same as the ICA model without fine-tuning. This is because the post-adjustment process adjusted the ICA result up and down to smooth the curve, making the accumulated

Fig. 7. Bivariate distributions of the diurnal and nocturnal base loads in the target days

TABLE I MEAN VALUES AND STANDARD DEVIATIONS OF THE DISTRIBUTION OF THE BASE LOAD 15-MINUTE POWER CONSUMPTION

Parameters Actual ICA Proposed μ [ 15.40

3.16 ] [ 12.12

2.69 ] [ 16.45

3.22 ]

Σ [ 79.99 13.12

13.12 8.02 ] [ 32.13 5.08

5.08 1.76 ] [ 91.30 10.56

10.56 3.75 ]

TABLE II PERFORMANCE COMPARISON FOR DIFFERENT LOAD DISAGGREGATION METHODS

Benchmark Models Proposed Model

Average ICA Case 1 Case 2 Case 3

nMAE (%) 15.48 14.80 13.75 13.87 12.92 nEE (%) 16.35 15.82 14.07 15.73 14.21 std(nMAE) 7.52 9.32 6.09 7.42 5.87

energy consumption of the HVAC load remain approximately the same. Finally, the standard deviation of nMAE for the proposed model is smaller than that of the benchmark model, showing a more robust and consistent estimation performance.

This trend can also be found in Fig. 8, where the empirical distributions of nMAE are shown. Note that each error observation is collected by averaging the resultant errors of each customer on multiple days to show the robustness of model across multiple customers. While nMAE of the ICA method without fine-tuning are distributed almost uniformly from 0.05 to 0.3, the error distribution of Case III of the proposed model is centered around 0.1.

IV. CONCLUSION

In this paper, we present an ICA-based HVAC load disaggregation model enhanced by a fine-tuning process. This

(a) Proposed

(b) ICA

Fig. 8. Empirical distributions of nMAE of 70 customers

approach enables the HVAC load disaggregation using lowresolution smart meter data as inputs. We first proved that by using the mild day load profiles, one can successfully extract the base load profile and approximate the distribution of the base load electricity consumption. Then, we show that the ICA method can be used more effectively on the residual load profiles (computed by subtracting the base load from the hot day load profiles) instead of on the hot day load profiles directly. Next, through fine-tuning, the preliminary results obtained by the ICA method can be further improved. The proposed method is compared with benchmark models and shows consistent performance across multiple customers. Our future work is to apply the method to disaggregate load profiles with behind-the-meter solar photovoltaic systems and electric vehicle charging loads.

REFERENCES

[1] R. Bonfigli, E. Principi, M. Fagiani, M. Severini, S. Squartini, and F. Piazza, “Non-intrusive load monitoring by using active and reactive power in additive factorial hidden markov models,” Applied Energy, vol. 208, pp. 1590–1607, 2017.

[2] W. Kong, Z. Y. Dong, D. J. Hill, J. Ma, J. Zhao, and F. Luo, “A hierarchical hidden markov model framework for home appliance modeling,” IEEE Transactions on Smart Grid, vol. 9, no. 4, pp. 3079–3090, 2016.

[3] L. Yan, W. Tian, J. Han, and Z. Li, “efhmm: Event-based factorial hidden markov model for real-time load disaggregation,” IEEE Transactions on Smart Grid, 2022.

[4] Y. Yang, J. Zhong, W. Li, T. A. Gulliver, and S. Li, “Semisupervised multilabel deep learning based nonintrusive load monitoring in smart grids,” IEEE Transactions on Industrial Informatics, vol. 16, no. 11, pp. 6892–6902, 2019.

[5] P. Comon, “Independent component analysis, a new concept?” Signal processing, vol. 36, no. 3, pp. 287–314, 1994.

[6] Y. Zhu and S. Lu, “Load profile disaggregation by blind source separation:

A wavelets-assisted independent component analysis approach,” in 2014 IEEE PES General Meeting— Conference & Exposition. IEEE, 2014, pp. 1–5.

[7] M. Liang, Y. Meng, N. Lu, D. Lubkeman, and A. Kling, “Hvac load disaggregation using low-resolution smart meter data,” in 2019 IEEE Power & Energy Society Innovative Smart Grid Technologies Conference (ISGT). IEEE, 2019, pp. 1–5.

[8] “https://www.pecanstreet.org.”

[9] A. Hyvärinen and E. Oja, “Independent component analysis: algorithms and applications,” Neural networks, vol. 13, no. 4-5, pp. 411–430, 2000.